# FINDER\_7E\_46\_8\_400\_0212

## `FINDER_7E_46_8_400_0212` (FB)

FUNCTION\_BLOCK FINDER\_7E\_46\_8\_400\_0212

InOut:

| Scope       | Name                        | Type               | Initial      | Comment                                                                                                           |
| ----------- | --------------------------- | ------------------ | ------------ | ----------------------------------------------------------------------------------------------------------------- |
| Input       | `xEn`                       | `BOOL`             | TRUE         | Enable / disable communication ( TRUE = enabled )                                                                 |
| Input       | `byUnitId`                  | `BYTE`             | 0            | Address of the device                                                                                             |
| Input       | `xUpdateActual`             | `BOOL`             | FALSE        | <p>Update of actual values (on every rising edge<br>)</p>                                                         |
| Input       | `xResError`                 | `BOOL`             | FALSE        | Reinitialization of the outputs 'eErrorCodeCom' and 'xErrorCodeDev' to the error-free state (on each rising edge) |
| Input       | `xActiveEnergyImportPart`   | `BOOL`             | FALSE        | <p>Reset of the meter ‘Active energy received -<br>Partial measurement - in kWh’ (on each rising edge)</p>        |
| Input       | `xActiveEnergyExportPart`   | `BOOL`             | FALSE        | <p>Reset of the meter ‘Active energy delivered - Partial measurement<br>- in kWh’ (on each rising edge)</p>       |
| Inout       | `ModbusClient`              | `ModbusClientBase` |              | Client of the device                                                                                              |
| Output      | `stDeviceType`              | `STRING`           |              | Type of device                                                                                                    |
| Output      | `stSerialNum`               | `STRING`           |              | Meter serial number (10 ASCII characters)                                                                         |
| Output      | `rU1N`                      | `REAL`             |              | Phase voltage L1 - N in XXX V                                                                                     |
| Output      | `rU2N`                      | `REAL`             |              | Phase voltage L2 - N in XXX V                                                                                     |
| Output      | `rU3N`                      | `REAL`             |              | Phase voltage L3 - N in XXX V                                                                                     |
| Output      | `rIL1`                      | `REAL`             |              | RMS value of phase current L1 in X.X A                                                                            |
| Output      | `rIL2`                      | `REAL`             |              | RMS value of phase current L2 in X.X A                                                                            |
| Output      | `rIL3`                      | `REAL`             |              | RMS value of phase current L3 in X.X A                                                                            |
| Output      | `stDirection`               | `STRING`           |              | Direction of energy flow (Import / Export)                                                                        |
| Output      | `rPowerFactorL1`            | `REAL`             |              | Power factor L1 in X.XX                                                                                           |
| Output      | `rPowerFactorL2`            | `REAL`             |              | Power factor L2 in X.XX                                                                                           |
| Output      | `rPowerFactorL3`            | `REAL`             |              | Power factor L3 in X.XX                                                                                           |
| Output      | `rActivePowerL1`            | `REAL`             |              | Effective active power L1 in X.XX kW                                                                              |
| Output      | `rActivePowerL2`            | `REAL`             |              | Effective active power L2 in X.XX kW                                                                              |
| Output      | `rActivePowerL3`            | `REAL`             |              | Effective active power L3 in X.XX kW                                                                              |
| Output      | `rReactivePowerL1`          | `REAL`             |              | Effective reactive power L1 in X.XX kvar                                                                          |
| Output      | `rReactivePowerL2`          | `REAL`             |              | Effective reactive power L2 in X.XX kvar                                                                          |
| Output      | `rReactivePowerL3`          | `REAL`             |              | Effective reactive power L3 in X.XX kvar                                                                          |
| Output      | `dwActiveEnergyImportTotal` | `DWORD`            |              | Active energy received - Total - in kWh                                                                           |
| Output      | `dwActiveEnergyImportPart`  | `DWORD`            |              | Active energy received - Partial measurement - in kWh                                                             |
| Output      | `dwActiveEnergyExportTotal` | `DWORD`            |              | Active energy delivered - Total - in kWh                                                                          |
| Output      | `dwActiveEnergyExportPart`  | `DWORD`            |              | Active energy delivered - Partial measurement - in kWh                                                            |
| Output      | `dwActiveEnergyTotal`       | `DWORD`            |              | Active energy - Total - in kWh                                                                                    |
| Output      | `dwReactiveEnergyTotal`     | `DWORD`            |              | Reactive energy - Total - in kvar                                                                                 |
| Output      | `rFWVersion`                | `REAL`             |              | Firmware version of the device                                                                                    |
| Output      | `rHWVersion`                | `REAL`             |              | Hardware version of the device                                                                                    |
| Output      | `xAlarm`                    | `BOOL`             | FALSE        | General fault ( TRUE = fault )                                                                                    |
| Output      | `xAlarmCom`                 | `BOOL`             | FALSE        | General fault - communication ( TRUE = fault )                                                                    |
| Output      | `eErrorCodeCom`             | ModbusErrorCode    |              | Error code - communication ( 0 = no error )                                                                       |
| Output      | `stErrorCodeDev`            | `STRING`           |              | String with the numbers of the active device errors                                                               |
| Output      | `xBusy`                     | `BOOL`             |              | Communication indicator ( TRUE = communication )                                                                  |
| Input Const | `tTimeUpdateActual`         | `TIME`             | TIME#1m0s0ms | <p>Update interval for operations influenced by the input<br>'xUpdateActual'</p>                                  |
